AMP Modular Cat.6 SL
Modular jacks shall be un-keyed, [unshielded or shielded], 4-pair, RJ-45, and shall fit in a .790″ X .582″ opening. Modular jacks shall terminate using 110-style pc board connectors. Each modular jack shall be wired to [T568A or T568B]. The 110-style insulation displacement connectors (IDC) shall be capable of terminating 22-24 AWG solid or 24-26 AWG stranded conductors.
The insulation displacement contacts (IDC) shall be paired, with additional space between pairs, to improve crosstalk performance. Modular jacks shall utilize a secondary PC board, separate from the signal path, for crosstalk compensation. Each modular jack shall meet the [TIA/EIA-568-C.2, Category 6 or ISO/IEC 11801 Class E] performance standards and the requirements listed in the following table.